I recently dug up the conduit from the garage to fix a known "knick" in the power line running from the office junction box to the garage. The electrcial came by and used a special spray from a can, and then wrapped it real nice with electrical tape. He confirmed that it is fully resolved and that this is ready to re-bury. I will be gathering the supplies and re-burying the conduit this weekend coming up. Then once that is done, and the hole is drilled through the garage container floor, we will then commission the electrician to revisit and complete all the electrical wiring needed to light the garage for a final wrap up event.